In order to supply the stream heating of the industrial production and the stream heating of factory workers’ heating and ventilation of residences, the Changchun wheel foundry will build the industrial boiler room which located in Changchun city. This project is sole construction project of Changchun wheel foundry.
The design main contains the selection of boiler, the feed-water treatment system of boiler, blow-in system of boiler and the coal transportation and cleaner system of boiler. In this project, we choose 2 stream boilers in SHL20-1.25/350-A which were produced in Hangzhou boiler factory and the coal was produced in Tonghua, Jilin province. We adopt single-stage sodium converter that the countercurrent regeneration in the fixed bed to do soften treatment. The selection of entire water spray heat deaerator was due to adoption of the thermal deaerator. In the blow-in system, the air-blower and the forced draught blower cooperate with each other. The air-blower was used to overcome resistance of wind and burning equipment; of the boiler itself, which contains flues, chimneys, and duster. In the process of the flue gas treatment, we adopt the HNPSC serious of internal and external spray chiseled ashlars’ water film duster to remove dust by desulphurization, so that the flue gas can reach the effluent standard. Because of large quantity of using coal in the coal tra